15A NCAC 18C .0203 PUBLIC WELL WATER SUPPLIES
Any site or sites for any water supply well to be used as a community or non-transient, non-community water system shall be investigated by an authorized representative of the Division of Environmental Health. Approval by the Division is required in addition to any approval or permit issued by any other state agency. The site shall meet the following requirements at the time of approval:
(1) The well shall be located on a lot so that the area within 100 feet of the well shall be owned or controlled by the person supplying the water. The supplier of water shall be able to protect the well lot from potential sources of pollution and to construct landscape features for drainage and diversion of pollution.
(2) The minimum horizontal separation between the well and known potential sources of pollution shall be as follows:
(a) 100 feet from any sanitary sewage disposal system, sewer, or a sewer pipe unless the sewer is constructed of water main materials and joints, in which case the sewer pipe shall be at least 50 feet from the well;
(b) 200 feet from a subsurface sanitary sewage treatment and disposal system designed for 3000 or more gallons of wastewater a day flows, unless it is determined that the well water source utilizes a confined aquifer;
(c) 500 feet from a septage disposal site;
(d) 100 feet from buildings, mobile homes, permanent structures, animal houses or lots, or cultivated areas to which chemicals are applied;
(e) 100 feet from surface water;
(f) 100 feet from a chemical or petroleum fuel underground storage tank with secondary containment;
(g) 500 feet from a chemical or petroleum fuel underground storage tank without secondary containment;
(h) 500 feet from the boundary of a ground water contamination area;
(i) 500 feet from a sanitary landfill or non-permitted non-hazardous solid waste disposal site;
(j) 1000 feet from a hazardous waste disposal site or in any location which conflicts with the North Carolina Hazardous Waste Management Rules cited as 15A NCAC 13A;
(k) 300 feet from a cemetery or burial ground; and
(l) 100 feet from any other potential source of pollution.
(3) The Department may require greater separation distances or impose other protective measures when necessary to protect the well from pollution; the Department shall consider as follows:
(a) The hazard or health risk associated with the source of pollution;
(b) The proximity of the potential source to the well;
(c) The type of material, facility or circumstance that poses the source or potential source of pollution;
(d) The volume or size of the source or potential source of pollution;
(e) Hydrogeological features of the site which could affect the movement of contaminants to the source water;
(f) The effect which well operation might have on the movement of contamination; and
(g) The feasibility of providing additional separation distances or protective measures.
(4) The lot shall be graded or sloped so that surface water is diverted away from the wellhead. The lot shall not be subject to flooding.
(5) When the supplier of water is unable to locate water from any other approved source and when an existing well can no longer provide water that meets the requirements of this Subchapter, a representative of the Division may approve a smaller well lot and reduced separation distances for temporary use.
History Note: Authority G.S. 130A‑315; 130A‑318; P.L. 93‑523;
Eff. January 1, 1977;
Readopted Eff. December 5, 1977;
Amended Eff. July 1, 1994; September 1, 1990; September 1, 1979.