15A NCAC 18C .0903 DEAD‑END WATER MAINS
Where installation of dead‑end water mains cannot be avoided, a hydrant or a valve of adequate size for flushing shall be installed at the terminal end of the line. The flush valves shall have an above‑ground discharge and shall be protected from contamination.
History Note: Authority G.S. 130A‑315; 130A‑317; P.L. 93‑523;
Eff. January 1, 1977;
Readopted Eff. December 5, 1977;
Pursuant to G.S. 150B-21.3A, rule is necessary without substantive public interest Eff. November 23, 2015.